FIELD ASSEMBLY (Continued)
A step down transformer with a nominal 125 volt primary winding and from 15 to 30 volt secondary can be used for this
purpose. The primary should have a cord with a plug for a wall receptacle. The secondary should have extension leads
with insulated probes. With the alternator operating, plug into the wall outlet and insert the probes momentarily into the
125 volt convenience outlet. For equipment not furnished with the outlet, touch the probes to the connection of L1 and
L2. A momentary contact is all that is required. The transformer assembly can be purchased from the factory at a
nominal cost if not available locally.